Subscribe to our magazine for only £75 / US$133 / €102. Enter your information and our Subscriptions Manager will contact you.
Thank you for subscribing to our magazine. We are just just processing your request....
The Journal for Employee Protection
The Journal for Employee Protection
Enter your information and a sales colleague will be in contact with you soon to discuss your paid magazine subscription.
Emergency safety showers and eye wash stations are essential for sites where workers could come into contact with hazardous chemicals. In some environments providing this life saving equipment can be challenging, for instance a consistent supply of potable water cannot be guaranteed, or a tepid temperature can be difficult to maintain due to extreme ambient temperatures.
In these instances, emergency tank showers provide a viable solution. However, because emergency tank showers can go unused for extended periods of time, the water held in the tanks may become stagnant. This makes it susceptible to bacterial growth and if not properly treated and maintained can become a source of infection.
The tepid water temperature range required by EU and International standards (ANSI Z358.1 and EN15154) is another contributing factor. These standards stipulate that the water temperature in emergency safety showers must be between 16°C (60°F) and 38°C (100°F). Unfortunately, bacteria thrive in temperatures between 20°C (68°F) and 45°C (113°F).
OSHA identified certain bacteria as a potential source of infection in safety showers. These include:
Not everyone is vulnerable to these bacteria, but for those that are the resulting infections can be quite severe.
ANSI requires that safety showers and eyewash stations are tested at least once a week. This weekly activation process displaces stagnant water in the pipework and flushes out corrosion or sediment, reducing the risk of bacteria growth. The duration of the flushing depends on the volume of water within the unit but it is recommended to follow a real-life emergency scenario to ensure that the equipment is able to run for the required time.
The UK Health and Safety Executive developed a guide to help with controlling the risks of exposure to Legionella bacteria. It recommends developing a risk assessment profile for all man-made water systems, including safety showers and eye/face wash equipment. A routine inspection cycle should include sterilising strainers, shower heads and nozzles.
Organise a Hughes service plan to ensure that your safety showers are disinfected regularly to reduce the risk of bacterial growth.
Hughes Safety Showers treats all the emergency tank showers with a self-sanitizing treatment (SST) on the tank walls prior to leaving the manufacturing facility. The SST inhibits the growth of bacteria, keeping shower users safe from infection. Annual re-treatment is recommended and is part of all annual services provided by Hughes.
An additional operational treatment for sanitizing emergency tank shower water is the use of Hydroclenz. This product provides constant protection against infestations of pathogenic bacteria. The ceramic component serves as an oxidizing agent, while the noble metal acts as an ionizing agent, working together to kill the bacteria. They also aid in inhibiting corrosion and scale build-up.
Contact Hughes Safety for more information or to receive a quote. Our sales team can advise you on the best solution for your application as well as the regulatory requirements that are relevant to your industry.
Download the PDF of this article here
Established in 1968, Hughes have built a reputation for innovative engineering design, stringent quality standards and compliance with European and International standards.
You’re in safe hands with Hughes Safety Showers.
Activate Your Safety Shower Weekly
A Press Release by Hughes Safety
Enter your information to receive news updates via email newsletters.
Terms & Conditions |
Copyright Bay Publishing